1.Product introduction of Screwed Fire Hydrant Valve
The landing valves are oblique type with flanged inlet and are manufactured to comply to BS 5041 Part 1 standard with delivery hose connection and blank cap complying with BS 336:2010 standard.
2.5”BSP or BSPT male thread
2.5”BS 336 Female coupling with plastic cap & chain
Valve Seat Test at 16.5 Bar,and Body Test at 22.5 Bar
Water Flow Rate
8.5 L/S @ 4 Bar Outlet Pressure as per BS5041 standard
Body material :copper alloy
Hand wheel material:grey cast iron
Blank cap material:plastic,copper alloy or aluminium as per customer’s requirement
Possible to replace the gland seal when under pressure with the valve fully closed
Disc facing rubber is of replaceable type
Valves are provided with a strap and pad lock so that the hand wheel can be secured to counter unauthorized use
The hand wheel is Iron blank
Body is red Painting with RAL3000
4.Product details--see attached
Q: How about your packing?
A:Polybag one product into stronger paper carton,finally packing the goods with the pallet
Q: What is your terms of payment?
A: In normal condition, 30% T/T in advance, balance before shipment. But other methods are discussable.
Q: Are you trading company or manufacturer ?
A: We are factory,so we can supply the most favourable price.
Q:What’s your MQO and delivery time?
A:100pcs for each item,delivery time is around 30-35days after received the TT advance.
We're Here to Help